Nine points of maintenance of air shower room
In this paper, by the spirit of the clean air shower room experts on some of the wind shower door equipment maintenance knowledge, how to maintain the procurement of wind shower door? As long as the following small methods on it, and the operation is very simple, direct their own operations on it, basically do not have to pay another technician to repair, simply to save money.
The following is the maintenance of the wind shower door 9 points;
First, pay attention to the temperature of the equipment should not exceed 50 degrees, and the use of open flame is prohibited.
Second; regular maintenance of the electrical circuit, if there is failure to refer to the electrical schematic for maintenance.
Third. Replace the high efficiency filter, remove the ball plate, remove the high efficiency filter, according to the original high efficiency filter specification model to replace the new high efficiency air filter. When installing, be sure to mark the arrow on the HEPA filter. The arrow points to the direction of the airflow. And to ensure a good seal to prevent leakage.
Fourth; when the wind speed hours should first check early efficiency air filter surface is black, black if that pre filter dust more, the resistance increases, which should be removed early efficiency air filters in non-woven cleaning or to replace them.
Fifth; the use of equipment to determine the technical specifications of equipment, if not meet the requirements of technical parameters should be promptly dealt with.
Sixth, according to the actual use, the initial effect of the air filter in the filter removed.
Seventh; when the replacement or cleaning of non-woven fabrics, still can not improve the speed of the air filter is said to have been blocked, resulting in increased resistance, it should replace the HEPA filter.
Eighth; after the replacement of the high efficiency filter, it is necessary to confirm that the frame has no leakage phenomenon, and the dust particle counter is used for detection, and the technical index can be carried out normally.
Ninth, the door of the door of the wind shower regularly, so that the electronic lock and the lock hole alignment, so as not to lock pin stuck.
GZLJ Star products: Air filter HEPA filter MEPA filter Primary efficiency filter Bag filter Carbon activated filter Air shower Air shower room Air shower channel FFU HEPA outlet Pass box Clean bench Fan filter box Clean shed<
Copyright: Guangzhou Lingjie Air Purification Equipment Manufacturing Co.,Ltd. 粵ICP備13059951號-2 Management Entry