Common fault handling air shower
Air shower manufacturers (www.mrhoganrocks.com, Lee 15914315027)
One, the power switch. Usually the wind leaching room there are four places you can cut off the power supply:
The power switch 1, the wind leaching outdoor box;
The control panel 2, the wind leaching room box;
4, the wind leaching room on both sides of the outer case (where the power switch can prevent an emergency cut off the power supply, effectively improve the staff’s personal safety). When the power indicator light barrier, preventing to check more than four wind leaching room power supply.
Two, the wind leaching room fan does not work. When the wind leaching room does not work, the emergency switch the first time to check the air shower outdoor box is cut, such as determining the cut off, one hand gently press, rotation can be loosely to the right.
Three, the wind leaching room fan reversal or air shower wind speed is very small, please be sure to check the 380V three-phase four wire circuit is connected in reverse, the general air shower room manufacturers factory installation will have special electrical connected; such as reverse connect the line source of wind leaching room, it will cause the air shower room fan doesn’t work or reversal of wind leaching room wind speed decreases, the circuit board that would burn the entire air shower; recommend the use of wind leaching room enterprises do not lightly to replace wiring, for sure to move production needs, please contact the air shower room manufacturers solve. 
Four, the wind leaching room not shower, in addition to the above three points, also need to check the wind leaching room inside the box of the emergency stop button is pressed, such as emergency stop button for the color, the wind leaching room is not blowing leaching; to press the emergency stop button can work normally.
Five, the wind leaching room not automatic induction shower, please check the wind leaching room box under the angle of the right optic system, see the light device is installed correctly, such as light on both sides are opposed and light can be normal, automatic induction shower.
Six, the wind leaching room used for a period of time when the wind speed is low, the beginning of HEPA filter, please check the wind leaching room is too much dust, such as is replace the filter. (the wind leaching room primary filter is generally 1-6 months a replacement, the replacement of a air shower filter is generally 6-12 months)
Air shower manufacturers (www.mrhoganrocks.com, Lee 15914315027) spirit clean
From：Guangzhou Lingjie Air Purification Equipment Manufacturing Co.,Ltd. http://www.mrhoganrocks.com